1 Inch Diaphragm Type Shut OffGasValve for Use with Scentr y III Control Systems
1 inch diaphragm type gas valve. Use with any Safety First USA Scentry III gas detector systems , i.e. the SFGVC or GFRAB ( No control systems included ). UL listed gas valve interfaces with Scentry III-GFRAB home gas detector (not included) for natural gas and propane or the Scentry III-SFGVC automatic gas valve controller (not included). Protect home or building from a gas explosion or fire from gas leaks. Note: This is only the gas valve.
Electrically operated gas shut off valve opens and closes on demand signal from a thermostat or other controlling device. For use with natural gas and LP gas at pressures up to 0.5 psi. This White Rodgers replacement is a compression spring closing and soft seat construction gas valve.
Safety First Scentry III GVM Gas Valve Specifications:
Dimensions: 4.06 inches high by 2.63 inches wide by 3.5 inches long
Voltage: 24 VAC, 60 Hz
Inlet/Outlet Size: 1.0 inches x 1.0 inches.
BTU Capacity: 505,000
Amp Rating: 0.4A, 7.5W
Electrical Connections: 30 inches
Replaces White Rodgers Part # 2509-258
GFRAB and the GFA require use of this valve or the equivalent 1/2 or 3/4 inch GVD valves.
Maximum inlet pressure: 0.5 psi
Permissible ambient (surface) temperature is: -40 to 175 degrees F, CSA, -40 to 140 degrees F, UL
Two 30 inch leads
Warranty: One year by Safety First USA
CSA (AGA/CGA) Certificate number 2295211656058
Australian Gas Association Certificate number 4235